View and Download Bosch DB operation and installation manual online. DB Network Card pdf manual download. Bosch DB Pdf User Manuals. View online or download Bosch DB Operation And Installation Manual. Office Manuals and free pdf instructions. Find the office and computer equipment manual you need at ManualsOnline.
|Published (Last):||5 February 2017|
|PDF File Size:||12.70 Mb|
|ePub File Size:||5.7 Mb|
|Price:||Free* [*Free Regsitration Required]|
The AC Fail Time entry was modified to allow additional programming flexibility. Try calling the pager yourself first and listening to the length of time it takes to get a beep allowing you to enter touch-tone information. Determine whether this command center or any command bsoch with the same address setting, emits the Exit Now exit delay tone during the delay arming of an area s.
This only applies for Users through Use this function to test the communication link between the control panel and the central station receiver s. This Program Entry Guide shows the programming options for each product handler. U User Group Default: Restrict Opening and Closing Reports for this area.
When used in this configuration, the strike relay contacts must be supervised. Three to six digits s9210b to 9 Enter the User number you are programming. This occurs when the door is physically held open past the shunt time and the extend time has a value greater than bosxh see the Access Program Entry Guide for the door assigned to this area in CC Assign Door. The next 16 bits second and third byte are used for the U Card Data. If a printer is connected, data does not print.
Bosch DB Manuals
To enable alarm verification on a point, program Resettable as D9201b. Each user can be assigned the same or different authority level by area.
Com Port Selection within HyperTerminal Reports Relay Reset Event. Use this setting for telephone systems where specified.
A Force Armed Default: To disable remote programming, enter Blank in both Answer Armed and Answer Disarmed d9210v in this section. Reports low battery power.
REX must not be used for emergency exit applications. Do not connect initiating devices to a Keyswitch point. Consider the application carefully before using the bypassable option. EN 35 Table It shuts off the bell when the programmed number of minutes expires.
Command centers assigned to associate areas, when used in conjunction with shared areas, should have the CC Scope programmed to encompass the shared area. This relay provides a steady output until the user at the command center acknowledges the trouble. Send Report Use this function to view prior alarm, trouble, and supervisory activity occurring since the last time the system armed. The user must use a passcode to silence a Fire Bell.
After ten e9210b, the control panel goes into communications failure and Comm Fail Route displays on the command centers. Enter up to sixteen characters of text for this user group. The availability of each handler is indicated in Table 4. No Restart bell output with each alarm event.
Db Overview SDI input and output. EN 11 The control panel is pre-programmed with a 7-second dial tone detect period. These numbers are called Sub-user ID Codes. DB Program Entry Guide It is not, however, related to the D2910b Time used for smoke detectors.
Bosch D9210B Access Control Interface Module Fire Alarm
Ordered Separately A power supply, and 1 DB. Each option is listed with: Enter it in U Mstr Site. Reports restoral of point bus after failure. Pager Display Fields  1 EN 25 2 3 4 Account number Event policy Event numberFire Alarm Event User number, point number, or relay number Vosch account number must contain four numeric digits.
Mounting Page 17 – Step 5: Any time an event is generated and routed to a numeric pager, the control panel attempts to call the numeric pager once for each message in the queue. The armed state does not change in other areas, and the armed state does not change if the area is already in the perimeter instant or disarmed state.
Failure to follow this programming requirement results in improper operation of the D